A customer in Bridgewater, NJ called Pipe Works Services because their air conditioning unit was not blowing out cold air. This was a fequent issue. Our technician Zack discovered that the system was low on refrigerant. Zach then performed a leak search and found that there was a leak in the evaporator coil, and the compessor suffered some damage
The best option for this customer was to install a new Lennox A/C system.
our service area