An existing customer in Basking Ridge, NJ called into Pipe Works Services and said that his air conditioning is not working. He also said he smelled a bit of a burning smell outside near his condenser.
When Pipe Works Services technician Alan and Richard arrived at home, they noticed that there was a small clog in the condensation line causing the EZ trap to trip off. They fully inspected the system and diagnosed the blower motor and main control board to be in good working order but did notice the system was 4 pounds low. They added 410A refridgerant to the system and corrected the minor leak at Schrader core valve.