Gfci for rear gutter heat trace trips randomly.
Found old gfi and touching ground and neutral wiring.
Checked heat cable, found 2 locations where Cable is bare.
Brought issues to owners attention, recommended replacement of cable and gfci outlet.
Customer chose to replace outlet and patch cable are spots.
our service area