Performed heating psa’s and checked water heater. Also performed plumbing inspection, see check sheets. Replaced customer supplied filter and also replaced water panel for humidifier. Mentioned age of boiler to customer, he is going to wait until they redo the basement. Recommended replacement of the water softener, he is going to hold off on this as well. Left systems in normal operation.
our service area