Upon diagnosis found high limit tripped, found once reset that upon furnace sequence of operations it’s all established except blower operation, tested capacitor for proper MFd reading and it’s below 6% threshold of capacitor, will provide customer with options on repair. However please keep in mind unit is from 1996 and replacement option should be consider. Upon testing unit with new MFD 7.5 rated cap. Found that units electrical main logic board does not transfer power to the blower on the heat terminal 120v strip. This is leading to a series of different issues.
our service area