Perform heating PSA. Drain steam boiler , remove and clean pressure switch and pig tail. Along with sight glass and sight glass isolation controls. Re install all components. Fill water in boiler to proper level. Run boiler and test for proper operation. All electrical components working properly along with all ignition components, performed combustion analysis and all is with safe range. Customer has active leak coming from hall way radiator. Angle isolation valve needs to be replaced. Will provide pricing to replace valve. Also needs cartridge replaced for upstairs hall bath. Advised customer due to visual condition of shower valve looks corroded and aged. May need to replace shower valve if not able to extract cartridge from valve body.
our service area