Our technician found upon further diagnosis found respectable transformer tripped. Shortage in wiring is present concluded thermostat wiring inside wall is compromised.
Ran new wire from thermostat into basement below through floor joists and into boiler junction box. Rewired accordingly. and tested for proper function all is working well at this time.
our service area