Customer states he has no heat for one of the zones, blower motor is not coming on. Upon diagnosis found that blower motor is seized to start, allowed unit to go thru it’s cycle and motor is barely turning the wheel, tested for outgoing 120 power at Heat terminal of blower and we were getting power. Establish that blower motor is no good and will require replacement. Will provide customer with proper operations and functions. Presented customer with options, customer opted for basic replacement, supplied and installed new OEM blower motor, tested for proper operations and functions.
our service area