Customer states he has no heat. After further diagnosis failure at sequence of operation after igniter glows. 24 volts line voltage at solenoid plug as well as adequate incoming gas pressure to gas valve. Solenoid appears to have failed and new gas valve is needed. Advised customer furnace is very old and should be replaced.
our service area