Customer states his furnace was shutting on and off however upon arrival furnace was operating properly. Customer states it’s been operating properly since he restore power. Tested micro amp reading to flame sensor and it’s registering proper reading. He also checked for proper sequence of operations, proper voltage to gas valve is present, proper wc” pressure is present.
The technician advised customer if he has issue in the future to not restore power right away rather look at LED indicator lights and see if they are throwing off an error code which we can use as a starting point, no issues present right now furnace running perfectly fine at this time. Previous CO test was done and no high level of PPM found.
our service area