Our technician went to a home in Chatham, New Jersey to perform a yearly maintenance. He cleaned the flame rod, cleared the condensate drain hoses, check the condensate trap, tested the amp draw on motors, and perform combustion analysis on system. The system is still operational and the filter and humidifier pads are good. The second floor system has a cleaned flame rod, cleared condensate drain hoses, check condensate trap, and tested the amp draw on motors.He also performed a combustion analysis on the entire system.
our service area