Customer states she is having a leak from boiler. Upon arrival found floor soaked and back wall to garage wet as well.
After further diagnosis found burner assembly under casting of boiler heavily rotted and corroded. Burner tubes are also showing signs of corrosion.
Removed jacket from right hand side of boiler and sections of cast are heavily corroded and rotted showing signs of leak.
Boiler piping is not leaking relief valve is not dripping pressure and temps on boiler are within proper ranges.