The technician performed maintenance on 3 furnaces. He also changed the attic furnace filter which was overdue. He found signs of leaking on the induction motor and tested all safeties, electrical, gas pressure and exhaust. The tech found the 1st floor and basement system with filters and humidifier pads all brand new. At this time all systems seem to be working and no repairs suggestible at this time customer should start getting estimates for replacement units as they are old.
our service area