Customer states leak at boiler. Upon inspection found safety relief valve is leaking. Confirmed boiler pressure is within range and fast fill / back flow preventer is working proper. Also expansion tank is working proper. Advised customer on options. Removed and disposed of old safety relief valve after draining boiler. Installed new component. Filled and purged boiler.
our service area