Our technician provided and installed a new pressure regulator valve along with an expansion tank. He then tested for proper operation and function. He also installed a low water cut off for the boiler system along with external pressure and temperature gauge. He installed new gaskets for all the connections on the supply and return system. The tech performed an extensive boiler system service including cleaning off heat exchanger. He then bled the entire system and test for proper operation and function.
our service area