Upon diagnosis found low levels of refigirant on system and obvious leak by liquid side port connecting to service valve.
Will re braze leak an test system with nitrogen and pull proper vacuum will then remove charge accordingly and test for proper operations and functions.
Made all necessary repairs system operational.
Please be advised outdoor condenser coil has excessive debris build up chemical cleaning required. Will provide estimate to customer.
our service area