2nd floor ac unit not working. Found jackets for furnace off unit. Upon inspection found bad capacitor for indoor blower motor. Replaced capacitor and tested unit. Indoor blower motor has weak resistance on windings. It is on its way out indoor unit and coil from 1987 very antiquated equipment. Advised customer if any issues occur in the future replacement will be needed.
our service area