Our technicians Odin and Jose installed a 3 ton air handler and condenser with a pad and blue stones. They flushed the lineset, and when we tested the equipment we noticed that the 24v transformer burned out after 1 hour. After trouble shooting they found the issue was a thermostat that was bad so we ordered a new transformer. After they put the new one in the equipment it started working. Additionally, they also installed a new thermostat for pressure.
our service area