An existing customer in Basking Ridge, NJ called Pipe Works Services and said that his air conditioning is not working. He also said he smelled a bit of a burning smell outside near his condenser.
When Pipe Works Services technicians Alan and Richard arrived home, they noticed that there was a small clog in the condensation line causing the EZ trap to trip off. They fully inspected the system and diagnosed the blower motor and main control board to be in good working order but did notice the system was 4 pounds low. They added 410A refrigerant to the system and corrected the minor leak at the Schrader core valve.
Air Conditioning Repair in Basking Ridge, NJ