Look at electric service/panel to verify its large enough for work. Panel has 4 spaces left, 150 amp service.
The job will require 4 spaces, and the service is large enough for the work, however there will be no room for expansion in the future and there are plans to finish the basement. It is highly recommend that the service be upgraded to 200 amp with 40 space panel. 18’ Drop, 200 amp meter and 40 circuit main breaker panel. Add price for generator interlock setup for panel to replace small generator transfer panel.
our service area