Our technician met with the homeowner about his electrical panel shorting when attempting to reset breaker. Upon further inspection he found the breaker oxidized. The tech installed a new 2 pole breaker to attempt to restore power to condenser. This option replaces the oxidized breaker. He stripped wires back for a clean connection. Upon starting the system our tech found all to be working properly and spoke with owner about the surge protection which was also installed.
our service area