Customer states she continues to not have hot water,
Or thatgas pressure has been increased that can be ruled out, verified proper gas pressure and it’s within manufacture specs.
Proceeded to contacting NTi manufacture and after relating all combustion information and numbers along with gas pressures, and flame signal on high fire.
We established that software for boiler Board must be upgraded to new software allowing the flame threshold to sustain the combustion.
our service area